Availability: In stock
The Context Plus XP95 manual call point is tough, durable and highly visible.
A single alarm LED is provided on the call point. This LED is controlled, independently of the call point, by the control and indicating equipment (CIE).
The call point?s address is set at the commissioning stage by means of a seven-segment DIL switch.
Call points can be remotely tested from the CIE by transmission of a single bit in the communications protocol. Call points respond by providing a value of 64 which corresponds to the alarm value. The CIE should recognize this response as a test signal and should not raise a general alarm.
The call point is available in two versions:
Part number: 55000-905IMC for surface mounting, incorporating the call point assembly (55000-900IMC), and a back box (26729-107).